|Payment Terms:||L/C,T/T,Western Union,MoneyGram|
|Supply Ability:||10000 Piece/Pieces per Week|
|Place of Origin:||Zhejiang China|
|Delivery Detail:||3-10days to received payment|
|Packaging Detail:||1PC/inner box, 40PCS/Standard Carton|
TEH-D06 Pulse Sparker/Ignitor
TEH-D06 Gas oven's controlling system applys the micro-controlling chip,has function stability, the anti-interference ability waits for a characteristic by force,the apply to petroleum gas, the coal gas,various gas firing flame sounds usage.
Output High Voltage 16KV ignition
1. Capatble of automatic ignition when it is out(the time for ingnition is within 8 seconds)
2. Automatic Light and deep alarm is given when failure ingnition.
3. Off(on) indicator, burning(operating) indicator, to be switched automatically.
4. The gas electromagnetic value will be automatically switched off if the ignition fials again.
Main Technical Parameter
*Working Voltage: 220V/50Hz
*Consumed Power: <10W
*Igniter Voltage: >16KV
*Ignition Distance: 3~5mm
*Operational Environment:Temperature-20C—60C Humidity≤95%
*Time Error: ±0.5%
*Power Output: DC24V electromagnetism valve output
AC220V fan output
*Appearance Size:126×87×54(39)(mm) Mounting Distance:74mm
TEH-D06 Digital Gas Sparker User Manual
The new version controlling system of TEH-D06 Gas Sparker chooses the
micro-processor, which will be more precise, steadier and more anti-Interference than
the old version. It can be applicable for lighting natural gas equipments or coal gas
1. Specification about TEH-D06
l Power Supply: 220V / 50 HZ
l Power Consumption: ≤ 10W
l High Voltage Spark(When lighting gas): ≥ 12KV
l Space between ignition electrodes: 3-5mm
l Using environment conditions:
Temperature: -20°C - 60°C Humidity: ≤95% RH
l Output Power:
2 DC 24V outputs for Electromagnetic valves, AC 220V for Fan
l External dimensions: 126*87*54(39mm)
2. Functions: When power-on TEH-D06 Sparker. The program would follow from
step1 to step4.
Step1. Start by signal Buzzer and LED for 3 seconds
Step2. After 1 second, ignition electrodes start to spark, gas Electromagnetic
and Fan working.
Step3. If gas would be sparked up then stop sparking immediately, gas
valves open and Fan working continually.
Step4. If gas cannot be sparked up for 8 seconds, then the TEH-D06 alarm
system wouldstart-up (Red LED flashing and Buzzer alarming), and
ignition electrodes sparkwould be stopped and gas Electromagnetic
valves would be closed and Fan
would stop working, In this situation TEH-D06 stop working until
operator restart the TEH-D06 Sparker.
3. Caution for Users
* Ignition electrodes earthing conductor and Electromagnetic valve earthing
to strictly connect to earth.
* During theWorking time, the surface of TEH-D06 maybe exits static electricity.
For more information Please Visit our website:www.eidison.com
Yueqing Eidison Trading Co., Ltd.
54 Changzheng Rd.,
Liushi, Yueqing, Zhejiang,
Mobile: 0086 137 8011 8727
Phone: 0086 577 6171 9886
Fax: 0086 577 6175 5366