|Payment Terms:||T/T,Western Union,visa,master card,e-checking|
|Supply Ability:||1000 Unit/Units per Month|
|Applicable Industries:||Hotels,Garment Shops,Building Material Shops,Manufacturing Plant,Machinery Repair Shops,Food & Beverage Factory,Farms,Restaurant,Home Use,Retail,Food Shop,Printing Shops,Construction works ,Energy & Mining,Food & Beverage Shops,Advertising Company|
|Place of Origin:||Shandong China|
|Brand Name:||KING VITAL|
|Item:||Waste Oil Burner/Diesel Oil Burner|
|Max.Output Heat:||50,000Kcal/h (200,000Btu/h)|
|Nozzle:||siphon brass 1*1.0mm|
|working pressure:||0.5bar (7psi)|
|fuel:||all kinds of waste oil,waste engine oil,soybean oil etc|
|application:||boiler,furnace,oven,air heater,grain dryer etc|
|business type:||original manufacturer|
|Packaging Detail:||1 unit double carton box with foam for express to door package size:58x53x42cm G.W:30kg|
Diesel Oil Burner for The Bakery Oven 36-60KW
1.malfunction and solution:
Mal button lights,quick flicker turns to slowly flicker.
Press reset button to see if burner is back to work.If not,take off the photo cell and wipe.
Mal button is alway light,reset button can't press.
In this case,power off and connect the power again.
It is a self protection,because new burner,there is no oil in oil pump and filter.Pump can’t supply oil within 2 mins,oil float gives message to print board,to shut down the burner for protection.
Heat button is lighting,then light the mal button.
There is too much water in the oil.
use the valve in the bottom of the small tank to leak water.
Stilling oil for a night,let me water and oil seperate.
Ignition rod is striking fire,but no fire.
Use the tool to remove the nozzle,check if it has been blocked,change the rubber pad too.
The tool and rubber pads are also with the burner,we send you for this situation.
If you meet other problem,contact us first .
2.Have you improved and innovated your product?
As a factory,we improve and innovate all the time,we take customers requirment seriously.For example:
We insulate copper in demand of NZ customer need.
We change the print board's programme to reach 30s purge.some countries have demand for that.
We change the manual air flap to automatic system.To low down the noise.
We use one air compressor for two or three air solenoid system,to reduce the cost for customer.
If you have any requirement for burner,please let me know.
3.Customers have their own oil system,no need of oil pump system.Is that ok?
Yes,it's ok.Please let me know first.To see if we have to change the print board accordingly.
4.Do customers need to prepare the pre-filer?
No.We have it with the burner.If you have your own ideas,then it's ok.
5.Comparing waste oil burner within air pump,some diesel modified burner and other waste oil burner brand,what's the difference?
We are true waste oil system,differ from waste oil burner within compressor,diesel modifed burner or other brand.
|Kingwei Waste Oil Burner Catalogue|
(Liter per hour)
|KV03||2-3||14-55||30,000||0.1t boiler,furnace,oven etc|
|KV05||3-5||30-60||50,000||0.1-0.2t boiler,furnace,air heater etc|
|KV10||6-8||80-120||100,000||0.3t boiler,air heater,grain dryer etc|
|KV20||12-15||150-200||200,000||0.4t boiler,air heater,sand dryer etc|
|KV30||15-21||210-270||300,000||0.5t boiler,oven,dryer etc|
|KV40||30-40||230-360||400,000||0.6t boiler,reactor etc|
|KV50||35-45||230-460||500,000||0.8t boiler,dryer,reactor etc|
|KV60||40-60||450-560||600,000||1.0t boiler,dryer,reactor etc|
|KV90||70-80||850-1000||900,000||1.5t boiler,dryer,reactor etc|
|KV120||100-120||1000-1300||12,00,000||2.0t boiler,dryer,furnace etc|
|KV180||180-260||1500-1800||18,00,000||3.0t boiler,dryer,furnace etc|
|KV240||200-350||2000-2400||24,00,000||4.0t boiler,grain dryer etc|
|KV360||400-540||3000-4000||36,00,000||6.0t boiler,grain dryer etc|